Simple Thermostat ETV
DIN Rail Thermostat with Setback Mode - Type ETV
OJ DIN Rail Thermostats – with setback mode for control of electrical heating: floor, ceiling and radiant. The ETV is suitable when remote control of the system is required. It is a compact thermostat saving space on the panel. ETV has setback temperature function, which is activated via external timer. Setback temperature is fixed 5ºC.
- Suitable when remote control of the system is required
- Setback temperature function, activated via external timer
- Compact and space-saving
What is the maximum length of the sensor cable?
In general, we recommend a maximum cable length of 50 meters, the length might be shorter. Read the instructions for the precise maximum length.
How can I cure the E2 error message?
"E2" means defective, damaged or disconnected floor sensor. Sensor resistance should be 10 or 12 kOhm at 25°C (77°F). The onstruction or quick guide holds informatiom for the specific thermostats.
Where to connect the ground wire of floor mats?
The ground wire in the floor mat must be connected directly to the ground wire of the supply.
What is the recommended night setback?
The recommended night setback is max 5°C/41°F
Does the adaptive function reset when making a factory reset?
Yes the adaptive function is reset during a factory reset.
Know How Creates is our promise to you: we use our insight and expertise to find the right solution.
Find the latest Floor Heating Electric News from OJ Electronics here.
Intelligent control results in maximum comfort with low energy consumption.
Dialogue and close cooperation is the shortest way to a perfect solution.