Clock Thermostat ICD3
4-event clock thermostat - with one sensor
Electronic thermostat for control of temperature by means of a sensor placed either externally in the floor or built into the thermostat. ICD3 can also operate in regulator mode, for renovation purposes where a floor sensor can not be used.
The thermostat has a built-in clock - calendar with power backup and comes with built-in 4-event program for automatic comfort and setback temperature. The graphical display has an unique user interface with new graphical menus and button-based navigation for easy programming and readout of data.
- Easy menu navigation and programming in 5 different languages
- Adaptive control ensuring comfort temperature at the required time
- Built-in clock function for automatic comfort and setback temperatures
- Built-in schedule ready for use. Delivered with factory-set program
- Thin clock thermostat, giving the installer an easier job
- Graphical backlit display for ease of use
Where to connect the ground wire of floor mats?
The ground wire in the floor mat must be connected directly to the ground wire of the supply.
What is the recommended night setback?
The recommended night setback is max 5°C/9°F
Does the adaptive function reset when making a factory reset?
Yes the adaptive function is reset during a factory reset.
E2 - How can I cure this error message?
"E2" means defective or disconnected floor sensor. Sensor resistance should be 12kOhm at 25°C (72°F).
What is the maximum lenght of the sensor cable?
In general, we recommend a maximum cable length of 50 meters.
Know How Creates is our promise to you: we use our insight and expertise to find the right solution.
Find the latest Floor Heating Electric News from OJ Electronics here.
Intelligent control results in maximum comfort with low energy consumption.
Dialogue and close cooperation is the shortest way to a perfect solution.